CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||28 July 2004|
|PDF File Size:||7.22 Mb|
|ePub File Size:||15.53 Mb|
|Price:||Free* [*Free Regsitration Required]|
Detector tubes must be pulled and their alignment confirmed if results indicate any abnormalities. Battery Type as installed: G Test to ensure lights function for a duration equal to design criteria?
S36 detectors whose labels are missing, faded and unreadable, or painted are considered failed and require replacement. Refer to Appendix F2 ; iv A battery capacity meter test.
Intelligibility clarity of voice messages confirmed. Confirm field device free of damage. Proper light function – power loss?
The communicator is trouble free. Buildings – prior to freezing weather?
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
Battery Capacity as installed: Hangers and seismic braces inspected from floor level? Refer to Appendix F1 ; P iii Silent accelerated test. V Visual indicator test lamp test operates.
Visible signaling appliances tested? Once a month or so, take your vacuum on it’s lowest setting and utilizing a soft brush attachment, clean out the vents of the detector. Hose rack assembly pressure reducing valve partial flow test.
Standards Council of Canada
It’s a good idea to check the battery compartment every six months for leakage or corrosion on the terminals. Yes No Oil Pressure: Common visual trouble signal operates. Automatic transfer from alert to alarm signal cancel acknowledge operates on a two stage system.
Electrical components in service? Combination multi-criteria detectors inspected and tested? Monthly Inspection and Tests A Pilot lights are functioning? Displays are visible in the installed location. Annual Operate emergency starting means w536 power Trip circuit breaker if provided? Description of the function of each operating control and indicator on the fire alarm control unit.
Are all existing fire protection systems in service? Will racks swing out of the cabinet at least ninety 90 degrees? Adequate heat available to areas where wet cann is located? Identify zone, circuit number, or address.
Fire Alarm System Periodic Inspection (CAN/ULC-S)
Visual indicator test lamp test operates. This type of detector is best used in residential applications, as it provides extremely good early warning to smoldering type fires that tend give off dense smoke and noxious fumes. These units are vulnerable to electrical failures they won’t function in the absence of power. Catholic Umbrella Pool II. Plugging of sprinklers found during activation or alteration? Reconnect ancillary functions off site connections?
Full operation of adjustments such as pattern selection? Flame detectors inspected and tested. Vancouver, Richmond, and Langleythe individuals performing annual testing must be registered by ASTTBC or certified by an agency recognized by the local authority.